By: Gillian Hogarth | 0 Comment
Client delighted as BES brings disused high volume water supply borehole back into production.
In August 2016 Borehole Engineering Services (BES) received an order to refurbish a long disused water supply borehole which was drilled over 100 years ago. A previous CCTV inspection of the existing 790mm borehole lining had identified corrosion and surface water intrusion over the top 15mtr which could potentially allow undesirable bacteria to the structure. The video inspection also identified that the borehole which was originally drilled to 151mtr was now dipping at 142mtr due to the build-up of sediment over the years. The sediment was a potential source of turbidity and would need removing. The bottom section of the borehole also penetrated marls which also cause turbidity and the client wanted this strata grouted up following the removal of the sediment.
The work package consisted of Relining, Acidising, Scrubbing, Airlifting, Grouting and then carrying out a CCTV survey to demonstrate the condition of the refurbished production borehole. A new submersible pump and rising main was then to be installed and the borehole recommissioned.
A construction Phase Plan was drafted and signed off before works commenced.
The Client had previously removed the existing submersible pump and rising main which had been out of action for a considerable time.
BES was instructed to reline the top section of the borehole to a depth of 24mtr. A 693mm casing was selected for the relining. This casing was centralised within the original 790mm casing with steel centralisers welded at 3mtr intervals and 3no grout skirts were fitted externally near the base to assist in the subsequent grout installation. The relining casing was installed using a 35ton mobile crane with each 6mtr length being lifted into place, centralised and welded. Once the full string of casing was in position, it was secured on steel lugs while the grouting operation was carried out.
Mikolit 500 bentonite pellets were now introduced down the annulus and onto the top of the grout skirts and wetted. They were then allowed to swell and form a tight seal between the two casings. A slug of grout was then tremmied onto the top of the seal and this was allowed to set. Further grout was placed in stages until the annulus was fully grouted to the surface.
A DN700 PN16 slip flange was now placed over the 693mm casing and sat on top of the original 790mm casing before being fully welded to the 693mm casing.
An extension piece of casing was fitted to the newly placed flange thus raising the top of the casing out of the wellhead chamber for safety purposes during the acidising operations which can produce copious amounts of gas. 6 tons of hydrochloric acid was introduced into the borehole through a special pressure tested acidising headworks. The acid was introduced in 1 ton increments while monitoring for pressure fluctuations. Hydrochloric acid reacts vigorously with the Magnesian Limestone strata found in this location often causing a potentially dangerous pressure build up. In this instance no pressure build up occurred indicating that the Limestone was highly fissured. The acid reacts with the Limestone and burns its way through the fissures dissolving blockages and opening up channels allowing an easy route for groundwater to enter the borehole.
Acidisation creates loose debris from the dissolved sediments. The borehole casings also become encrusted over time. One method for removing this build up is to scrub the borehole walls with mechanical brushing action. As part of the works programme, the borehole was now scrubbed throughout with a steel wire brush. The 700mm diameter brush was fitted to 31/2” IF drill rods. This operation removed all loose encrustation from the sides of the borehole and casings ensuring that there were no loose elements to become dislodged and damage the submersible pump or to cause turbidity in the groundwater.
The scrubbing process creates copious loose material and sludge which falls to the bottom of the borehole. Air lifting is a good method for removing this unwanted debris. A main eductor pipe is lowered through the water table and near to the base of the borehole. A secondary smaller pipe introduces air fed by a compressor into the main pipe. The air enters the water column inside of the main pipe and rises rapidly causing suction at the base. The column of water rises bringing along loose debris from the base of the borehole and is ejected into a settlement tank at the surface. The process rapidly removes all loose debris leaving the borehole clean. This particular borehole had over 100 years of sediment in the base and extensive aggressive airlifting was necessary to ensure that it was cleaned throughout to the original drilled depth of 151.13mtr.
Part of the remit was to grout the bottom section of the borehole as this penetrated Marl strata known to cause turbidity. It was necessary to clean out this section of the borehole by air lifting before a proper grouting operation could be carried out. Once the borehole had been thoroughly cleaned, a tremmie pipe was installed to the base and grout was introduced backfilling from 151mtr to 140mtr. The grout was allowed to set and then the borehole was airlifted again to remove loose sediment arising from the grouting operation.
Our high definition full colour CCTV was used to obtain a full DVD record of the final result of the extensive rehabilitation operation for our Client.
Extension of Works;
At this stage, the results were so positive that the Client requested BES to manufacture a new working platform and headworks for the borehole. This was completed to the satisfaction of our Client.
The borehole was completed when a new submersible pump was installed along with an 8” ZSM stainless steel rising main to a depth of 126mtr.
Following commissioning works, our Client was delighted that their old disused borehole was now in an ‘as new’ condition pumping copious amounts of clean water into production line.
Borehole Engineering Services also offer the following services:
- Borehole CCTV Surveys
- Aquifer Testing to BS14686;2003
- Borehole verticality testing, Borehole Rehabilitation including scrubbing, acidization, airlifting, well development and chemical treatment to remove iron/ manganese build up.
- Decommissioning old and disused boreholes of any kind, even if they are brine, fresh water or artesian.
- Borehole relining service
- Retrieve most objects and tool blocking boreholes.
- Competitive prices for in hole equipment from all the leading manufacturers
- Hydro-fracturing for stimulating unproductive boreholes
- Service Contracts
- Rapid response for breakdowns
- Water samples taken
- Also a full complement of Drilling services available, visit drilcorp.com
For further information or to speak directly to a member of the team telephone 0191 5273970
BOREHOLES ARE OUR BUSINESS
BES carry out Borehole Remediation works and essential CCTV Surveys